Echelon SmartServer 1, SmartServer 2, SmartServer 3, i.LON 100, i.LON 600
All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 9.8
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: Echelon
- Equipment: SmartServer 1, SmartServer 2, i.LON 100, i.LON 600
- Vulnerabilities: Information Exposure, Authentication Bypass Using an Alternate Path or Channel, Unprotected Storage of Credentials, Cleartext Transmission of Sensitive Information
2. RISK EVALUATION
Successful exploitation of these vulnerabilities could allow for remote code execution on the device.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following Smart Server and i.LON products, which are network devices, are affected:
- SmartServer 1 all versions,
- SmartServer 2 all versions prior to release 4.11.007,
- i.LON 100 all versions, and
- i.LON 600 all versions.
3.2 VULNERABILITY OVERVIEW
An attacker can use the SOAP API to retrieve and change sensitive configuration items such as the usernames and passwords for the Web and FTP servers. This vulnerability does not affect the i.LON 600 product.
An attacker can bypass the required authentication specified in the security configuration file by including extra characters in the directory name when specifying the directory to be accessed. This vulnerability does not affect the i.LON 600 product.
The devices store passwords in plaintext, which may allow an attacker with access to the configuration file to log into the SmartServer web user interface.
The devices allow unencrypted Web connections by default, and devices can receive configuration and firmware updates by unsecure FTP.
- CRITICAL INFRASTRUCTURE SECTORS: Commercial Facilities, Critical Manufacturing, Information Technology
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Santa Clara, California
Echelon, working with Daniel Crowley and IBM’s X-Force Red team, self-reported these vulnerabilities to NCCIC.
Echelon recommends that affected users install SmartServer 2 Service Pack 7 (Version 4.11.007), to mitigate CVE-2018-8859, CVE-2018-8851, and CVE-2018-8855, which can be downloaded at the following link:
The following manual mitigation is also recommended:
For CVE-2018-10627, Echelon recommends affected users modify the WebParams.dat file.
Echelon recommends that the following mitigation is implemented until SmartServer 2 Service Pack 7 is installed:
- All SmartServer and i.LON 600 devices along with any servers using the SmartServer and i.Lon services should be installed behind a firewall or on a VLAN without other devices.
- Change the username and password during the initial installation of the affected products.
- Disable unencrypted services and secure encrypted services for the SmartServer or i.LON 100.
NCCIC recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
NCCIC reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
NCCIC also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS-CERT website in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to NCCIC for tracking and correlation against other incidents.
NCCIC also recommends that users take the following measures to protect themselves from social engineering attacks:
- Do not click web links or open unsolicited attachments in email messages.
- Refer to Recognizing and Avoiding Email Scams for more information on avoiding email scams.
- Refer to Avoiding Social Engineering and Phishing Attacks for more information on social engineering attacks.
No known public exploits specifically target these vulnerabilities.
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.