Rockwell Automation PanelView Plus 6 700-1500
All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
CVSS v3 8.6
ATTENTION: Remotely exploitable/low skill level to exploit
Vendor: Rockwell Automation
Equipment: PanelView Plus 6 700-1500
Vulnerability: Missing Authorization
The following versions of PanelView Plus 6 700-1500, graphic terminals and logic module products, are affected:
- 8.00-20140730, and
Additionally, Rockwell Automation reports that graphic terminals running OS 2.31 or greater are not affected by this vulnerability.
Successful exploitation of this vulnerability could allow an attacker to remotely access the device to potentially retrieve data or disrupt the availability of the device.
Rockwell Automation has released a security advisory found at the following link. A login is required to view the advisory.
Rockwell Automation reports that affected users should update to any of the following available firmware revisions that address the vulnerability:
- V7.00: Apply V7.00-20150209
- V8.00: Apply V8.00-20160418
- V8.10: Apply V8.10-20151026 or later
- V8.20: Apply V8.20-20160308 or later
- V9.00: Apply V9.00-20170328 or later
Downloads for the firmware revisions can be found at:
NCCIC/ICS-CERT and Rockwell Automation recommend that users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Block all traffic to EtherNet/IP devices or other CIP protocol-based devices from outside the manufacturing zone by blocking or restricting access to Port 2222/UDP and Port 44818/TCP using proper network infrastructure controls, such as firewalls, Unified Threat Management (UTM) devices, or other security appliances. For more information on TCP/UDP ports used by Rockwell Automation Products, see Knowledgebase Article ID 898270 found at https://rockwellautomation.custhelp.com/app/answers/detail/a_id/898270. A login is required to view the article.
- Help minimize network exposure for all control system devices and/or systems, and confirm that they are not accessible from the Internet.
- Locate control system networks and devices behind firewalls, and isolate them from the rest of the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices where they are used.
- When downloading updates, make sure the site or source of the update can be trusted.
ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies, that is available for download from the ICS-CERT web site.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability.
There is no authorization check when connecting to the device, allowing an attacker remote access.
Rockwell Automation self-reported this vulnerability.
Critical Infrastructure Sectors: Critical Manufacturing, Energy, Food and Agriculture, Transportation Systems, and Water and Wastewater Systems.
Countries/Areas Deployed: Worldwide
Company Headquarters Location: United States
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.