Siemens SIMATIC WinCC Flexible Weakly Protected Credentials Vulnerability
All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
Siemens has identified a weakly protected credentials vulnerability in SIMATIC WinCC flexible. Gleb Gritsai and Roman Ilin from Positive Technologies reported this issue directly to Siemens. Siemens has produced an update to mitigate this vulnerability.
This vulnerability could be exploited remotely.
Siemens reports that the vulnerability affects the following product:
- SIMATIC WinCC flexible: All versions prior to SP3 Up7.
Attackers capturing network traffic of the remote management module could possibly reconstruct user credentials.
Impact to individual organizations depends on many factors that are unique to each organization. NCCIC/ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Siemens is a multinational company headquartered in Munich, Germany.
The affected product. SIMATIC WinCC flexible, is a software package used for visualization and machine or small system operations. This product runs on standard PCs or on Siemens panel PCs. This product is deployed across several sectors including: Chemical, Energy, Food and Agriculture, and Water and Wastewater Systems. Siemens estimates that these products are used worldwide.
INSUFFICIENTLY PROTECTED CREDENTIALSa
The remote management module of SIMATIC WinCC flexible panels and SIMATIC WinCC flexible runtime transmits weakly protected credentials over the network. Attackers capturing network traffic of the remote management module could possibly reconstruct the credentials.
This vulnerability could be exploited remotely.
EXISTENCE OF EXPLOIT
No known public exploits specifically target this vulnerability.
An attacker with high skill would be able to exploit this vulnerability.
Siemens provides Update 7 for SIMATIC WinCC flexible 2008 SP3, which fixes the vulnerability, and recommends users to update to the new version. Update 7 can be found at the following location on the Siemens web site:
For more information on this vulnerability and more detailed mitigation instructions, please see Siemens Security Advisory SSA-526760 at the following location:
As a general security measure Siemens strongly recommends protecting network access to devices running SIMATIC WinCC flexible with appropriate mechanisms. Siemens advises configuring the environment according to Siemens operational guidelines in order to run the devices in a protected IT environment.
ICS-CERT recommends that users take defensive measures to minimize the risk of exploitation of these vulnerabilities. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT web page at: http://ics-cert.us-cert.gov/content/recommended-practices. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies, that is available for download from the ICS-CERT web site (http://ics-cert.us-cert.gov/).
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- a. CWE-522: Insufficiently Protected Credentials, http://cwe.mitre.org/data/definitions/522.html, web site last accessed June 09, 2016.
- b. NVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2015-1358, web site last accessed June 09, 2016.
- c. CVSS Calculator, https://www.first.org/cvss/calculator/3.0#CVSS:3.0/AV:N/AC:H/PR:N/UI:N/S... , web site last accessed June 09, 2016.
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.