Siemens SIPROTEC Denial-of-Service Vulnerability
All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
Siemens has identified a denial-of-service vulnerability in the SIPROTEC 4 and SIPROTEC Compact devices. This vulnerability was reported directly to Siemens by Victor Nikitin from i‑Grids LLC Russia. Siemens has produced a new firmware update to mitigate this vulnerability.
This vulnerability could be exploited remotely.
Siemens reports that the vulnerability affects the following versions:
- SIPROTEC 4 and SIPROTEC Compact product families
- All devices that include the EN100 Ethernet module version V4.24 or prior.
An attacker could remotely cause a denial of service by exploiting this vulnerability.
Impact to individual organizations depends on many factors that are unique to each organization. NCCIC/ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Siemens is a multinational company headquartered in Munich, Germany.
The affected products, SIPROTEC 4 and SIPROTEC Compact devices, provide a wide range of integrated protection, control, measurement, and automation functions for electrical substations and other fields of application. The EN100 module is used for enabling IEC 61850 communications with electrical/optical 100 Mbit interface for SIPROTEC 4 and SIPROTEC Compact devices. According to Siemens, SIPROTEC devices are deployed across several sectors including Energy. Siemens estimates that these products are used worldwide.
DENIAL OF SERVICEa
Specially crafted packets sent to Port 50000/UDP could cause a denial of service of the affected device. A manual reboot is required to return the device to service.
This vulnerability could be exploited remotely.
EXISTENCE OF EXPLOIT
No known public exploits specifically target this vulnerability.
An attacker with a low skill would be able to exploit this vulnerability.
Siemens has provided firmware update V4.25 for the EN100 module to fix the vulnerability.
The firmware update for SIPROTEC 4 can be obtained here:
The firmware update for SIPROTEC Compact can be obtained here:
For more information on this vulnerability and more detailed mitigation instructions, please see Siemens Security Advisory SSA-732541 at the following location:
ICS-CERT recommends that users take defensive measures to minimize the risk of exploitation of these vulnerabilities. Specifically, users should:
- Configure firewall rules to appropriately restrict traffic to affected devices on Port 50000/UDP.
- Monitor traffic to affected devices on Port 50000/UDP with an intrusion detection system (IDS).
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT web page at: http://ics-cert.us-cert.gov/content/recommended-practices. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies, that is available for download from the ICS-CERT web site (http://ics-cert.us-cert.gov/).
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- a. CWE-400: Uncontrolled Resource Consumption ('Resource Exhaustion'), http://cwe.mitre.org/data/definitions/400.html, web site last accessed July 21, 2015.
- b. NVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2015-5374, NIST uses this advisory to create the CVE web site report. This web site will be active sometime after publication of this advisory.
- c. CVSS Calculator, http://nvd.nist.gov/cvss.cfm?version=2&vector=AV:N/AC:L/Au:N/C:N/I:N/A:C, web site last accessed July 21, 2015.
For any questions related to this report, please contact ICS-CERT at:
Toll Free: 1-877-776-7585
International Callers: (208) 526-0900
For industrial control systems security information and incident reporting: http://ics-cert.us-cert.gov
ICS-CERT continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.