Schneider Electric Wonderware InTouch Access Anywhere Server Buffer Overflow Vulnerability
All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
Schneider Electric Wonderware has identified a stack-based buffer overflow vulnerability in the Wonderware InTouch Access Anywhere Server product. Schneider Electric has produced a security update that mitigates this vulnerability.
This vulnerability could be exploited remotely.
The following Wonderware InTouch Access Anywhere Server versions are affected:
- InTouch Access Anywhere Server, Version 10.6, and
- InTouch Access Anywhere Server, Version 11.0.
The successful exploitation of this vulnerability could cause a buffer overflow that may allow arbitrary code execution.
Impact to individual organizations depends on many factors that are unique to each organization. NCCIC/ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Schneider Electric corporate headquarters is located in Paris, France, and maintains offices in more than 100 countries worldwide.
The affected product, Wonderware InTouch Access Anywhere Server, provides access to InTouch applications through a web browser. According to Schneider Electric, Wonderware InTouch Access Anywhere Server is deployed across several sectors including Chemical, Critical Manufacturing, Energy, Food and Agriculture, and Water and Wastewater Systems. Schneider Electric estimates that the Wonderware InTouch Access Anywhere Server product is used worldwide.
STACK-BASED BUFFER OVERFLOWa
An attacker could cause a stack-based buffer overflow by requesting a nonexistent file that may enable the execution of arbitrary code.
This vulnerability could be exploited remotely.
EXISTENCE OF EXPLOIT
No known public exploits specifically target this vulnerability.
An attacker with low skill would be able to exploit this vulnerability.
Schneider Electric has released a security update that mitigates the stack-based buffer overflow vulnerability in Wonderware’s InTouch Access Anywhere Server product, Versions 10.6 and 11.0. Schneider Electric’s security updates for Version 10.6 and Version 11.0 are available at the following location with a user account:
Schneider Electric has released a security bulletin titled “InTouch Access Anywhere Server Security Vulnerability, LFSEC00000104” to announce the security update, which is available at the following location:
ICS-CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT web page at: http://ics-cert.us-cert.gov/content/recommended-practices. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies, that is available for download from the ICS-CERT web site (http://ics-cert.us-cert.gov/).
- a. CWE-121: Stack-based Buffer Overflow, http://cwe.mitre.org/data/definitions/121.html, web site last accessed January 8, 2015.
- b. NVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2014-9190, NIST uses this advisory to create the CVE web site report. This web site will be active sometime after publication of this advisory.
- c. CVSS Calculator, http://nvd.nist.gov/cvss.cfm?version=2&vector=AV:N/AC:L/Au:N/C:C/I:C/A:C, web site last accessed January 8, 2015.
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.