GE Proficy Vulnerabilities
All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
Researchers amisto0x07 and Z0mb1E of Zero Day Initiative (ZDI) have identified two vulnerabilities in the General Electric (GE) Proficy human-machine interface/supervisory control and data acquisition (HMI/SCADA) - CIMPLICITY application. GE has released security advisories, GEIP13-05 and GEIP13-06, to inform customers about these vulnerabilities.
These vulnerabilities could be exploited remotely.
The following GE Intelligent Platforms products are affected:
- Proficy HMI/SCADA - CIMPLICITY, Version 4.01 to 8.2, and
- Proficy Process Systems with CIMPLICITY.
CIMPLICITY CimWebServer does not check the location of the shell files that may allow an unauthenticated user to load shell code from a remote location rather than the default local directory.
Impact to individual organizations depends on many factors that are unique to each organization. NCCIC/ICS-CERT recommends that organizations evaluate the impact of these vulnerabilities based on their operational environment, architecture, and product implementation.
GE is a US-based company that maintains offices in several countries around the world.
According to GE, Proficy HMI/SCADA - CIMPLICITY is a Client/Server-based HMI/SCADA application, which is deployed across multiple industries.
The gefebt.exe component supplied with CIMPLICITY CimWebServer does not check the location of shell files being loaded into the system. By modifying the source location, an attacker could send shell code to the CimWebServer, which would deploy the nefarious files as a server-side script. This could allow the attacker to execute arbitrary code.
The CIMPLICITY Web-based access component, CimWebServer, does not check the location of shell files being loaded into the system. By modifying the source location, an attacker could send shell code to the CimWebServer which would deploy the nefarious files as part of any SCADA project. This could allow the attacker to execute arbitrary code.
These vulnerabilities could be exploited remotely.
EXISTENCE OF EXPLOIT
No known public exploits specifically target these vulnerabilities.
An attacker with a moderate skill would be able to exploit these vulnerabilities.
GE has produced an update that mitigates one vulnerability and made configuration changes to mitigate the other. Please reference the following GE Product Security Advisories for specific information on the vulnerabilities.
To address this vulnerability, all copies of the gefebt.exe files that are accessible from a Web client must be deleted or moved, so they are inaccessible. If the production Web configuration currently relies on gefebt.exe, changes to the server’s Web pages may also be desirable.
The GE Product Security Advisory, which provides additional guidance, is available here:
Download Proficy HMI/SCADA - CIMPLICITY 8.2 SIM 24 at:
The GE Product Security Advisory is available here:
NCCIC/ICS-CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
NCCIC/ICS-CERT also provides a section for control systems security recommended practices on the NCCIC/ICS-CERT Web page at: http://ics-cert.us-cert.gov/content/recommended-practices. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies. NCCIC/ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the NCCIC/ICS-CERT Technical Information Paper, ICS-TIP-12-146-01B—Targeted Cyber Intrusion Mitigation Strategies that is available for download from the NCCIC/ICS-CERT Web site (http://ics-cert.us-cert.gov/).
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to NCCIC/ICS-CERT for tracking and correlation against other incidents.
- a. CWE-22: Improper Limitation of a Pathname to a Restricted Directory ('Path Traversal'), http://cwe.mitre.org/data/definitions/22.html, Web site last accessed January 23, 2014.
- b. NVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2014-0750, NIST uses this advisory to create the CVE Web site report. This Web site will be active sometime after publication of this advisory.
- c. CVSS Calculator, http://nvd.nist.gov/cvss.cfm?version=2&vector=AV:N/AC:L/Au:N/C:P/I:P/A:P, Web site last accessed January 23, 2014.
- d. CWE-22: Improper Limitation of a Pathname to a Restricted Directory ('Path Traversal'), http://cwe.mitre.org/data/definitions/22.html, Web site last accessed January 23, 2014.
- e. NVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2014-0751, NIST uses this advisory to create the CVE Web site report. This Web site will be active sometime after publication of this advisory.
- f. CVSS Calculator, http://nvd.nist.gov/cvss.cfm?version=2&vector=AV:N/AC:M/Au:N/C:P/I:P/A:P, Web site last accessed January 23, 2014.
For any questions related to this report, please contact ICS-CERT at:
Toll Free: 1-877-776-7585
International Callers: (208) 526-0900
For industrial control systems security information and incident reporting: http://ics-cert.us-cert.gov
ICS-CERT continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.