Siemens Synco OZW Default Password
All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
Siemens has reported to ICS-CERT that a default password vulnerability exists in the Siemens Synco OZW Web Server device used for building automation systems. Siemens urges their customers to set a secure password on their device’s web interface. This vulnerability could be exploited remotely.
Siemens reports that the default password vulnerability affects the following Synco models:
- OZW672.01, OZW672.04, OZW672.16
- OZW772.01, OZW772.04, OZW772.16, OZW772.250.
For the listed products, all firmware versions prior to Version 4 do not force users to change their password on initial login.
An attacker could use the default password in these devices to gain unauthorized administrative access to the building automation network.
Impact to individual organizations depends on many factors that are unique to each organization. ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Siemens Synco OZW devices are used for remote operation and monitoring of building automation devices. The affected models offer interfaces that can be used over networks, such as the Internet.
Siemens Synco OZW devices are shipped with a default password protecting administrative functions. The installation procedure does not enforce a password change. This leaves a potential security gap in the asset owner/operator’s network.
This vulnerability could be exploited remotely.
Existence of Exploit
No known public exploits specifically target this vulnerability.
An attacker with a low-skill level could exploit these vulnerabilities.
Siemens has released a firmware update (Version 4) and security advisory (SSA-283911) for the OZW672 and OZW772 devices that enforces a password change at initial login.2 Customers may upgrade to this firmware version, but this is not required to change the default password on existing devices. Siemens urges customers to set a secure password on the web interface for all network devices.
ICS-CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks by performing the following tasks:
- Minimize network exposure for all control system devices. Critical devices should not directly face the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognize that VPN is only as secure as the connected devices.
The Control Systems Security Program (CSSP) also provides a section for control systems security recommended practices on the CSSP Web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the ICS-CERT Technical Information Paper, ICS-TIP-12-146-01—Cyber Intrusion Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- 1. CWE-262: Not Using Password Aging, http://cwe.mitre.org/data/definitions/262.html, Web site last accessed August 13, 2012.
- 2. Siemens password change at initial login, http://support.automation.siemens.com/WW/view/en/41929231/130000, Web site last accessed August 13, 2012
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.