Inductive Automation Ignition Information Disclosure Vulnerability
All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
ICS-CERT has received a report from Rubén Santamarta concerning a vulnerability in Inductive Automation’s Ignition software. Ignition is an updated version of FactoryPMI (Plant Management Interface), offered by Inductive Automation. This vulnerability allows unauthorized users to download files containing important information about the system and project.
ICS-CERT has worked with Inductive Automation and Rubén Santamarta to confirm this vulnerability, and Inductive Automation has issued a patch to address it. ICS-CERT has validated that this patch fully resolves this vulnerability.
Inductive Automation Ignition versions prior to Version 22.214.171.124 are affected.
Impact to individual organizations depends on many factors that are unique to each organization. ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Ignition is an updated version of FactoryPMI, offered by Inductive Automation. Ignition is a full featured human-machine interface/SCADA product used in a variety of industrial applications that is produced by Inductive Automation. According to Inductive Automation, Ignition has known deployments in North and South America, Europe, Australia, and across Asia.
According to the researcher’s report, the vulnerability is exploitable by connecting a specific Uniform Resource Locator (URL) address. The successful connection to this URL results in a prompt to download files containing important details about system and project information, including authorized usernames and password hashes.
This vulnerability is remotely exploitable.
Existence of Exploit
No known exploits specifically target this vulnerability.
Exploiting this vulnerability requires a low skill set.
Inductive Automation has produced Version 7.2.8 of the affected software available on the Inductive Automation Downloads website. Customers who are unfamiliar with the Inductive Automation upgrade routine should contact the vendor for assistance.
According to its website, Inductive Automation Support can be reached at (916) 456-1045 or email@example.com.
ICS-CERT encourages asset owners to minimize network exposure for all control system devices. Critical devices should not directly face the Internet. Locate control system networks and remote devices behind firewalls and isolate them from the business network. When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
The Control Systems Security Program (CSSP) provides a section for control system security recommended practices on the CSSP web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.