ICONICS GENESIS32 and BizViz ActiveX Stack Overflow
All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
Security researchers Scott Bell and Blair Strang of Security-Assessment.com have released a report detailing a stack overflow vulnerability affecting ICONICS GENESIS32 and BizViz products. The vulnerable ActiveX control, GenVersion.dll, is a component of WebHMI, which is incorporated in both GENESIS32 and BizViz products. Successful exploitation of this vulnerability allows remote arbitrary code execution.
ICS-CERT has confirmed that ICONICS has issued a patch that addresses this vulnerability. ICONICS confirmed that Security-Assessment.com has validated that this patch fully resolves this vulnerability.
According to ICONICS, GENESIS32 and BizViz (Versions 9 through 9.21) are affected by this vulnerability.
If successfully exploited, this vulnerability results in remote arbitrary code execution with privileges of the current user.
Actual impact to individual organizations depends on many factors that are unique to each organization. ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their environment, architecture, and product implementation.
ICONICS is a US based company that maintains offices in several countries around the world, including the US, UK, Netherlands, Italy, India, Germany, France, Czech Republic, China, and Australia.
The affected products, GENESIS32 and BizViz, are web based HMI SCADA systems. According to ICONICS, GENESIS32 is deployed across several sectors including manufacturing, building automation, oil and gas, water and wastewater, electric utilities, and others. ICONICS estimates that 55% of GENESIS32 installations are in the United States, 45% are in Europe, and 5% are in Asia.
Vulnerability (or Malware) Characterization
Vulnerability (or Malware) Overview
Users could be lured into visiting malicious sites using social engineering or phishing techniquesc.
This vulnerability is remotely exploitable using a specially crafted string sent to the “SetActiveXGUID” method.
Existence of Exploit
An exploit targeting this vulnerability is publicly available.
This vulnerability requires moderate skill to exploit. Social engineering techniques are also needed to exploit this vulnerability.
ICONICS has released a patch that addresses this vulnerability for each of the affected products. ICONICS recommends that users of GENESIS32 and BizViz install the patch entitled “WebHMI V9.21 Patch.”
ICONICS also plans to address this vulnerability in the upcoming version 9.22 update of GENESIS32 and BizViz. ICONICS expects this update to be available in June 2011.
ICONICS has updated their “Whitepaper on Security Vulnerabilities” to include details of this vulnerability.
For additional product support, users can contact ICONICS by phone at (508) 543-8600 or by e-mail at email@example.com.
ICS-CERT recommends that users also take the following measures to protect themselves from social engineering attacks:
- Do not click web links or open unsolicited attachments in e-mail messages
- Refer to Recognizing and Avoiding Email Scams for more information on avoiding e-mail scams
- Refer to Avoiding Social Engineering and Phishing Attacks for more information on social engineering attacks.
ICS-CERT encourages asset owners to minimize network exposure for all control system devices. Critical devices should not directly face the Internet. Locate control system networks and remote devices behind firewalls and isolate them from the business network. When remote access is required, use secure methods such as Virtual Private Networks (VPNs).
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
The Control Systems Security Program (CSSP) also provides a recommended practices section for control systems, on the US-CERT website. Several recommended practices are available for reading or download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
For any questions related to this report, please contact ICS-CERT at:
Toll Free: 1-877-776-7585
International Callers: (208) 526-0900
For industrial control systems security information and incident reporting: http://ics-cert.us-cert.gov
ICS-CERT continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.